Posted by Yoopersup:
from the ct cabinet to the ist main the Neutral is your bond, also install a bonding strap or jumper from XO in CT cabinet to cabinet. (Usually supplied by manufacturer of Cabinet. If not size a conductor using 250.66
Installing EGC would give you a parallel neutral as your also required to (...)
Posted by BLU:
Guys, Thanks for the comments! The term "back of meter" comes to us from utility company engineers, and apparently more than one panel can be connected to the back of the meter in a SFR.if the meter socket is less than 20-40 years old (depends on the service area). When I bought my house 20 (...)
Posted by NORCAL:
The one problem I see with mounting Plugmold® to the studs & butting the drywall to it, is that the drywall would be chewed up if one had to open up the Plugmold® for whatever reason.
BTW, always thought the Walker multi-outlet assembly was more user friendly then Plugmold® but have no idea if (...)